|Features||Web Browser Views||Setup|
|Network System Configurations||Application Examples||Demo Site|
DL8 시리즈 Web Browser Views
|Large sized buttons are placed for ease of operating on the small sized screen of a smart phone.|
Short trend and digital data displays are available to monitor analog, discrete and totalized pulse signals. Event log is also available to review alarm events. All the views can be quickly ready for use by simple setting.
•TREND VIEW SPECIFICATIONS
|Sampling rate||1 s / 5 s / 10 s / 30 s / 1 min / 5 min / 10 min / 30 min / 1 h / 1 day|
|Number of pages||8 pages|
|Number of chs||4 chs per page|
|Pen color||User defined (RGB)|
|Graph range||User defined (engineering unit value)|
|Number of samples||Max. 7200 points per ch|
|Scrollable charts||1 to 10 (720 samples @chart span)|
•EVENT LOG SPECIFICATIONS
|Analog signal||Alarm triggered when measured value passes across the setpoint.|
|Discrete signal||Alarm triggered when status changes.|
|Totalized count||Alarm triggered when pulse count exceeds the setpoint.
(Counter can be reset.)
|Pulse signal||Alarm triggered when measured value passes across the setpoint.|
E-mails can be sent when an event occurs.
Specific recipients and texts can be defined for each event condition.
|USING THE DL8 ORIGINAL TAGS|
|The DL8 original tags in an HTML file are automatically converted into corresponding text/data string by the DL8. Users who do not have technical knowledge of programming scripts can easily create an original data view. The DL8 User Defined View must be created and used under the user's sole responsibility, including its display components and functions.|
•Simulated Imagery. View samples are not provided by M-System.